Fish meal factory WWTPview Blue Foot Membranes
Animal waste, Other
About Fish meal factory WWTP
- Technology: 2 bar Back Pulsable PVDF Flat sheet from Blue Foot Membranes
- Number of IPC® membrane modules: 1 IPC® 80 Module
- Application: fish meal wastewater treatment
- Start up: December 2019
In order to evaluate the effectiveness of the IPC® MBR membrane modules, a pilot plant was built and started up in the Kojima Sustainable Fisheries fish meal factory by Rematec. This factory is evaluating MBR technology for their challenging wastewater because of the need to reuse water and comply with the stringent discharge limits in the Osaka Prefecture. This was achieved by a Membrane Bioreactor pilot using one single IPC® membrane module.
In this product evaluation study, MLSS concentrations ranging from 8-16.000 mg/L MLSS were tested together with the backwash protocols. Net fluxes of 30-40 L/m2.h were reached and this is considered to be about 1.5 to 2 times above average net fluxes.
It was observed that the cake layer was cleared sufficiently by the backwashing every time at the end of the cycle, even at the high MLSS concentrations.
About this page
This page was last updated on 04 May 2022
Information on this page may have been supplied by third parties. You are reminded to contact any third parties to confirm information is accurate, up to date and complete before acting upon it. TheMBRSite.com accepts no liability for information provided by third parties, actions taken on the basis of this information or information held on third-party websites.