Zhejiang Pharmaceutical WWTP
About Zhejiang Pharmaceutical WWTP
The new project was designed after several months’ tests in situ for determination of the best options to implement the depuration of a very complex mix of industrial wastewater. The designed solution comprises the use of all concrete previous tanks all together with a new anaerobic treatment as Primary Treatment, based on VALORSABIO’s technology UASB-PRO, and a Secondary Treatment based also on VALORSABIO’s technology, the JET-LOOP SYSTEM + MBR.
In parallel to the Secondary Treatment based on biological processes (JET-LOOP SYSTEM + MBR) was also installed a Chemical and Physical unit, able to flocculate and remove non-biodegradable substances present in the effluents.
The UASB-PRO installed and in operation since November 2011, uses an new pulse process for the wastewater feed, solving the old problems found in large UASBs, related with unbalanced and bad distribution of feed, preferential paths of flow inside the bioreactors and difficulties in stabilising the up-flow wastewater within the design range.
The operation of the UASB-PRO is now capable to reduce the COD loads by more than 80%, even in the case with the presence of a poorly biologically degradable influent, and produces a considerable volume of biogas, thus reducing the treatment OPEX and creating a return as electrical energy and hot water from the biogas cogeneration burn.
As for the JET-LOOP SYSTEM + MBR, the process is operating with low HRT (less than 25%) in comparison with previous conventional activated sludge process and produces an extremely high quality treated water, fully under the legal permits negotiated with the authorities agencies.
Notes on technology used:
The designed solution comprises the use of all concrete previous tanks all together with a new anaerobic treatment as primary treatment, based on VALORSABIO’s technology UASB-PRO, and a secondary treatment based also on VALORSABIO’s technology, the JET-LOOP SYSTEM + MBR.
Information on this page has been supplied by third parties and is not necessarily endorsed by The MBR Site. You must contact the third parties to confirm information is accurate and complete before acting upon it. The MBR Site accepts no responsibility for any action taken or costs incurred as a result of information on The MBR Site. The MBR Site accepts no responsibility for the content of third party websites. Any views expressed are those of the third parties and do not necessarily reflect the views of The MBR Site.